# [1]黄虎,李志浩,虞维平.风冷热泵冷热水机组除霜过程仿真[J].东南大学学报(自然科学版),2001,31(1):52-56.[doi:10.3969/j.issn.1001-0505.2001.01.012] 　Huang Hu,Li Zhihao,Yu Weiping.Dynamic Simulation of Air Cooled Heat Pump/Chiller under Defrosting Condition[J].Journal of Southeast University (Natural Science Edition),2001,31(1):52-56.[doi:10.3969/j.issn.1001-0505.2001.01.012] 点击复制 风冷热泵冷热水机组除霜过程仿真() 分享到： var jiathis_config = { data_track_clickback: true };

31

2001年第1期

52-56

2001-01-20

## 文章信息/Info

Title:
Dynamic Simulation of Air Cooled Heat Pump/Chiller under Defrosting Condition

Author(s):
Department of Power Engineering, Southeast University, Nanjing 210096)

Keywords:

TB65
DOI:
10.3969/j.issn.1001-0505.2001.01.012

Abstract:
Based on the analysis of the defrosting process of air cooled heat pump/chiller,dynamic simulation model is established for air cooled heat pump/chiller operating under defrosting condition. The model is solved by using the method of quality guiding. The result of dynamic simulation is compared with that of experiment. It is found that the dynamic simulation is feasible for studying defrosting process of air cooled heat pump/chiller deeply. It is also useful for improving the performance of the unit working in winter.

## 参考文献/References:

[1] 黄虎,束鹏程,李志浩.中央空调中热泵的应用和节能.能源技术,1998(4):35～37
[2] 黄虎,束鹏程,李志浩.风冷热泵冷热水机组结霜工况下工作过程动态仿真及实验验证.流体机械,2000(3):49～52
[3] 蒋能照.空调用热泵技术及应用.北京:机械工业出版社,1997.126
[4] Krakow K I,Lin S.Yan Dr-ING I.An idealized model of reversed-cycle hot gas defrosting-part　2:experimental analysis.ASHRAE Trans,1992,98(1):462～474
[5] 丁国良.小型制冷装置动态仿真与优化研究:[学位论文].上海:上海交通大学动力系,1993
[6] 黄虎,束鹏程,李志浩.风冷热泵冷热水机组结霜工况下运行特性的实验研究.流体机械,1998(12):43～47